Tankless (Demand) Water Heaters
Installation Case Study with Photos, Commentary, and Payback Calculator
In May, 2006, we replaced our two gas, tanked water heaters with two gas tankless (a.k.a. "demand," or "instantaneous") heaters. We had two heaters because our home is a large ranch style. One heater supplied the bedroom area and the other served the kitchen sink, dish washer, and laundry. These old heaters were 12 years old. At the time of replacement, we also added two electric tankless heaters to supply sinks that were located a long way from the gas heaters. This was to reduce the time to get hot water at those faucets. So, let's count -- now we have four tankless water heaters.
Tankless heaters are more expensive than tanked heaters because they are more complex.
Old gas tanked water heater #1 (bedrooms)
New gas tankless water heater #1 (bedrooms)
Rinnai 2520 FFU
The cold water feed is the copper pipe coming down on the right, the hot water output is the pipe going up on the left, and the pipe going down is the high-pressure release (it's open at the bottom, just out of view).|
Notice that the hot water pipe is mostly 1.25-inch diameter. See the discussion about hot water delays, below.
The yellow pipe is the gas supply.
The temperature control uses a two-wire, low-voltage cable, so it could easily be moved to an upstairs location. (See detail photo, below.)
This unit serves three showers, two sinks, and a laundry. It works fine even if all three showers are in use.
Old gas tanked water heater #2 (kitchen)
(Not shown: dead mouse under heater)
New gas tankless water heater #2 (kitchen)
Rinnai 2520 FFU
|The new heaters have a small window (located near the middle of the cover) that allows you to view the firebox. You can see the gas flames modulate as you change the flow rate. The number of burners and the flame intensity change automatically as your demand changes.|
When you turn off your faucet, the burners extinguish immediately, but the exhaust fan continues to operate for a minute or two.
I designed a remote burner indicator for use near our kitchen sink. It consists of an IR detector poked into the viewing window, a Darlington amplifier circuit wired to an X10 transmitter, and a remote indicator connected to an X10 lamp module (photos below). This allows us to know if the flow rate is high enough to turn the heater on (preventing the water from unexpectedly going cold).
Installing a new vent pipe.
Fresh air goes in around the rim and exhaust air comes out through the center.
|Each of the gas water heaters has a "coaxial" pipe leading outside. This pipe draws combustion air in through the outside section and expels combustion gases via the inside section.
Our old tanked heaters would continue to heat for a long time after running a shower. The exhaust fan would cause annoying vibrations which were perceptible in the bedroom area. The tankless heaters shut off immediately when the water flow stops and the fan continues to run for only a short time. (The electric heaters are completely silent.)
Original gas meter and regulator (1/2 lb)
New gas meter and regulator (2 lbs)
|Tankless heaters consume more gas while running (compared to the tanked heaters), so we had to either increase the size of our gas meter and pipes or increase the gas pressure. Although the gas company charged $300 to replace our 0.5-lb gas meter with a 2-lb meter and regulator, we saved $600 of plumbing expense because we didn't have to replace our inside pipes with a larger diameter.
Our other gas appliances are two furnaces and a gas fireplace.
New electric tankless water heater #3
(located under the powder room sink)
Stiebel Eltron DHC 3-1
New electric tankless water heater #4
(located under the two master bathroom sinks)
Stiebel Eltron DHC 3-1
|The small electric heaters rely on the water flow rate to regulate the temperature.
That is limited via an adjustment inside the unit or by using a flow restrictor/aerator on the faucet. There's less water flow (both hot and cold) when using an aerator, but these heaters only serve a powder room and the master bathroom sinks.
We installed these units for convenience only: to decrease the wait time for hot water at the faucets. We'll never recover our investment (unless it increases the value of our home).
Our electric heaters are mounted in the basement, directly under the sinks. Such heaters are usually mounted in a cabinet closer to the faucet.
Rinnai 2520 FFU Internals
Stiebel Eltron DHC-1 Internals
One strange phenomena of tankless water heaters is the "cold water sandwich." After drawing hot water, the water pipes and the water heater will begin to cool down. If you start drawing hot water again before the water in the pipes has cooled, you'll still get some warm water, but the initial cold water entering the heater will not be heated. That cold water will eventually reach your tap. Thus, the water at the faucet will go from warm to cold and then to hot.
(There's a diagram, below.)|
If you're not prepared for this, you'll try to compensate by adjusting your faucet, causing yet more temperature fluctuations. And there's a minimum flow rate, below which the heater will turn off (but you won't know it until the water starts to run cold).
This was the reason I wired up a remote burner indicator as mentioned above (photos below). Rinnai's remote control does not indicate burner state.
Hot water capacity (50 deg-F rise): 0.6 to 5.3 gal/min
Temperature control: variable flame (automatic)
Maximum temperature setting: 140 deg-F
Efficiency rating: 87%
Hot water capacity (65 deg-F rise): 0.32 gal/min
Hot water capacity (49 deg-F rise): 0.42 gal/min
Temperature control: water flow rate (manual)
Maximum temperature setting: depends on flow rate
Efficiency rating: n/a (used to reduce time, not costs)
Rannai's temperature control panel
|Purchase and installation costs (all four units): $6,070 (plumber), $440 (electrician)|
How to compute the payback period when installing a tankless water heater instead of a tanked heater:
The calculator below will get you started on figuring your payback period. You'll need to measure water flow rates. There are two ways to do this.
In both cases, you are measuring the total water flow. This includes unheated cold water, but we correct for this by using the mixed, warm water temperature to compute the energy required. If you are able to measure only the hot water consumption (you installed a meter on your heater?), then use the hot water temperature.
This calculator also assumes that your tankless heater has an electronic ignition. If it use a standing pilot, enter "0" for your tanked pilot light usage (because you won't get any savings there).
Measure the inside diameter and the length of each pipe between your water heater and the faucet. For each length of pipe, square its radius, multiply by Pi (3.14159), and then multiply by the length. The result is cubic-inches (or cubic-feet). Add those volumes together to get the total volume of the standing water in your pipes. Then, repeat the computations, but use the smaller diameters. Multiply your current delay time by the ratio of the two volumes to compute your new delay. To this, add the time it takes the heater to get up to temperature.
For example, it will take about 7 seconds for water to flow through a 1-foot-long, 0.75-inch diameter pipe.
To measure the delays due to the heater internals and the water in the pipes after you have installed your tankless heater, go to the water heater, grab hold of the hot water pipe leaving the heater, and have somebody turn on the faucet. Write down the times when you feel the pipe getting hot and when your helper shouts out that the faucet is running hot. From this you can compute both delays. You cannot do much about the internal delay, but you can change the pipe diameters (local building codes permitting) to reduce the pipe delay.
A side effect of reducing the pipe diameter will be lower pressure at the faucet, especially if you are using two faucets at the same time that share part or all of the same pipe. So, consider this solution in light of your own installation and usage patterns.
Tankless Water Heater Summary:
Post Installation Improvements
It was frustrating to be turning down a faucet and discover 20 seconds later that the heater had turned off because the flow rate fell below the minimum. So, I installed sensors on the water heaters that operate indicators near the faucets showing if the heater is on or off. This allows the flow to be set as low as possible but still keep the water hot.
These improvements involve custom-built electronic sensors and indicators.
Sensors: The problem is finding a point to detect whether the heater is on or off.
Actual Results, Years Later (Jauary, 2012)
I've been tracking our gas bills every month, starting about five years before installing the water heaters and for another five years (and counting) afterwards. Here's a chart showing the summer months:
Notice the lines appear to bunch into two groups during June, July, and August (when our only gas usage is by the water heaters). As if by magic, the top group are the five pre-tankless years and the bottom group are the years since. Obviously, there's some savings there. Here are ballpark estimates based on the graph:
Links to More Information
Tankless Water Heater - What You Need to Know (About.com)
Tankless 101 A tutorial for the homeowner and the professional (profitableplumbing.com)
http://www.mge.com/business/saving/madison/PA_29.html (Madison Gas & Electric)
The following links assume tankless heaters have a standing pilot. One even states: "But gas-fired tankless heaters are only available with standing pilot lights." However, modern tankless, such as the Rannai units described above, have an electronic ignition.
http://www.eere.energy.gov/consumer/your_home/water_heating/index.cfm/mytopic=12820 (U.S. Dept. of Energy)
http://hes.lbl.gov/hes/makingithappen/no_regrets/waterheatertankless.html (Home Energy Saver, US DOE)
Disclaimer: Your results might vary. IANAP. jmat .. at .. mac .. dot .. com